|Place of Origin:||China|
|Brand Name:||Pearl Electric Co.,Ltd.|
|Certification:||KEMA, CE, CCC, ISO9001|
|Model Number:||PEC-S, SC(B) 9-15|
|Minimum Order Quantity:||1 unit|
|Packaging Details:||Seaworthy wooden packing|
|Delivery Time:||30days-50days ex-work|
|Payment Terms:||T/T, L/C|
|Supply Ability:||9000 units per year|
6.6 kV - Class , Dry Type Reator , Earthing , Stable Performance , High Reliabtility
Features & Advantages
To precisely calculate resonance frequency and intensity and avoid cavity resonance generated by the core structure during operation, simulation analysis is carried out for core mould design. Flexible connections are made between core and coils, core and bogie. With these measures adopted, the noise level is reduced by 10~15dB compared with the international standard.
During the HV winding design, rational structure is adopted to improve the electric distribution. With the lighting impulse wave simulation calculation and analysis being carried out with special auxiliary software, product's anti-lightning impulse capacity is greatly improved.
Tests before Putting into Service
.. Winding DC resistance test.
.. Check the core earthing conditions and the through-screw insulation conditions.
.. Insulation resistance test: usually the winding insulation resistance meets the following
In some high-humidity environment, the insulation resistance may be degraded. Usually,
the insulation resistance of each 1000V rated voltage should not be less than 2MΩ (at
25℃ for one minute). However, if condensation happens due to extremely damp
environment, the reactor must be dried before putting into service, no matter how
much the insulation is.
.. Externally-applied power frequency voltage-withstand test. The voltage applied
is 85% of the factory test voltage. The test duration is 1 minute.
.. Reactance measurement.
Installation and Putting into service
.. Place the product onto the installation foundation which is fixed with screw-down bolt.
There should be at least four anchoring screws on the foundation and anti-loosing
measures must be taken after the product installation.
.. Connect the earthing bolt on the base of the product with the earthing busbar.
.. Connect the outgoing cable terminal of the reactor with the capacitor busbar. The
connection should be flexible.
.. If the reactor is designed with taps, please select the proper tap and adjust the tap to
.. If the reactor is equipped with cooling fans, connect power supply cable and control
.. Check whether the above operations are finished and whether there are any foreign
objects within the transformer. Then, put the product into service.
.. Run the product for 60-minute trial operation. Then, put the equipment into service if
the trial operation is OK.
|Core:||Core-type Transformer||Cooling:||AN Or ANAF|
|Capacity:||10~2500KVA Or Customized||Rated H. V.:||6.6 Kv Or Customized|
|Rated L. V.:||0.4kv Or Customized||Impedance:||4~8% Or Customized|