|Place of Origin:||China|
|Brand Name:||Pearl Electric Co.,Ltd.|
|Certification:||KEMA, CE, CCC, ISO9001|
|Model Number:||PEO-S, S9~13,SZ11-M,SZ11|
|Minimum Order Quantity:||1 unit|
|Packaging Details:||Seaworthy wooden packing|
|Delivery Time:||50days ex-work|
|Payment Terms:||T/T, L/C|
|Supply Ability:||2.5 Million KVA/Year|
Three Phases , 220 kV - Class , Hight Capacity , Power Distribution Transformer , Two Winding
Pear ELectric's Product Introduction
Pearl Electric offers four types of 110kV class oil-immersed power transformer. The product are designed and manufactured according to customer's specifications. To know more about the product, please contact us. Product catalogs are available upon requirements.
The product has been widely applied in new and reconstruction projects of urban and rural power grids. Mass deployment of the products may achieve good energy-saving effects and reduce the atmospheric pollution. The product is especially suitable for the areas where the electric energy is insufficient, the load fluctuation is big and the daily maintenance is difficult. As the transformer adopts fully sealed structure and avoids contact with the air, it may run in the humid environment and is the ideal power distribution equipment for urban and rural power distribution network.
|By winding number||
110kV class 3-phase two-winding power transformer
110kV class on-load tap-changing power transformer
110kV class off-load tap-changing power transformer
High quality cold rolled grain-oriented silicon steel of high magnetic conductivity.
Oil sampling and testing (also refer ESKASAAF1)
a) Units with a highest voltage of 40 kV and above
One sample is required in each of the following cases:
1) during testing in the factory:
a particle test shall be performed before and after each filling of the transformer for factory testing. The particle count in oil shall be less that 1000/10ml for particles less than 2μm.
2) at time of take over:
all units delivered to site without oil, at least 7 days after in-situ oil processing has been completed, to test for dielectric strength, dissolved gas analysis (DGA), and acidity (A), but with the main emphasis on water content. Samples taken sooner will not necessarily reflect the correct water content (WC). Sample to be taken according to ESKASAAF1;
3) 2 days after energizing, to test for DS, WC, and DGA (Eskom responsibility);
4) after the 1st, 3rd and 6th month from date of energizing for DS, WC and DGA (Eskom responsibility);
5) thereafter, routinely for DS, WC, DGA and A as follows (Eskom responsibility):40KV-132KV
— power transformers of between 40 kV and 132 kV: - annually.
b) Units with highest voltages below 40 kV
Routine oil sampling and DGA of transformers in this group is normally not required, but this will be done at the discretion of the user (i.e. sampled on a “need only” basis). However, one sample to test for DS and WC, is required for acceptance purposes; before despatch from the manufacturer, or before commissioning on site. Records of the oil sample results shall be kept for future reference purposes.
c) On-load tap-changer diverter switches (all voltage categories)
A sample, to test for WC and DS only, shall be taken before commissioning and thereafter annually. This sample shall be taken from the tap-changer diverter conservator or diverter drain valve.
|Capacity:||6300~63000kVA Or Customized||Rated H. V.:||132kv Or Customized|
|Rated L. V.:||33kV/11kV Or Customized||Vector Group:||Dyn11 Or Customized|
|Impedence:||8-10% Or Customized||Cooling:||ONAN / ONAF Or Customized|