|Place of Origin:||China|
|Brand Name:||Pearl Electric Co.,Ltd.|
|Certification:||KEMA, CE, CCC, ISO9001|
|Model Number:||PEC-S, SC(B) 9-15|
|Minimum Order Quantity:||1 unit|
|Packaging Details:||Seaworthy wooden packing|
|Delivery Time:||30days-50days ex-work|
|Payment Terms:||T/T, L/C|
|Supply Ability:||9000 units per year|
22kV - 1250kVA Cast Resin Dry Type Transformer, Three Phases, Two Winding, Power Distribution
Cast Resin Dry Type Transformer, Low Noise, Low Loss and Low Partial Discharge.
Accessory for cast resin dry type transformer
The standard transformers is without enclosure, IP00 class. Type with enclosure is with protection level is IP20.
Temperature controller is equipped as per required. They can be installed on the transformer boday or wall of IP enclosure and reliable and convenient for users to check.
For on-load tap-changing transformers, please refer to the on-load tap changer Operation Manual. First, adjust the tap changer with the transformer switched off; if all indications are normal, then switch on the transformer.
1 Transformer with temperature control box and temperature indicator, please refer to respective operation manuals for detailed operation descriptions. After the temperature control box and temperature indicator is adjusted and all indications are normal, first switch on the transformer, then the temperature control box and temperature indicator.
2 Transformer should be switched on with no load. The peak switching inrush current could reach 10 times of the rated current. The fast motion protection set value should be higher than the switching inrush current.
3 When first switching on, avoid heavily loading the transformer. Beginning with a light load and increasing to a heavier load. While switching on the transformer, check for any abnormal noises.
4 Overload operation of the transformer should comply with IEC905 LOADING GUIDE FOR DRY-TYPE POWER TRANSFORMERS or the over-load curve in our Technical Manual.
5 The transformer can be switched on immediately after a period of service interruption. However, if humidity is high and condensation appears on the winding surface, the transformer can be operated again only after it is dried.
|I Basic Information|
|1||Rated Voltage ratio||kV||22kV / 0.433 kV|
|1.02||Applicable Standards||IEC 60076|
|1.04||Country of Origin||China|
|II Electric Performance|
|2.05||Number of phase||Three|
|2.06||Insullation Class||Class H|
|2.07||Temperature Rise (@40℃ ambient temperature)||K||125K|
|2.14||Load Loss (@120℃)||W||11300|
|2.15||Local Partial discharge||pC||<10PC|
|2.16||Impulse Withstand Voltage (HV/LV)||kV||75/0|
|2.17||Power Frequency Withstand Voltage
|2.18||Rated Duration of Short Circuit||s||2|
|4.02||Total mass (without enclosure)||kg||3030|
2 Applied Standard
GB/T10228 , GB1094.11 , IEC60076-11 , DIN42523
|Cooling:||AN Or Customized||Capacity:||1250KVA Or Customized|
|Rated H. V.:||22Kv Or Customized||Rated L. V.:||0.433kv Or Customized|
|Impedance:||6% Or Customized||Insulation Level:||H. V.: Li/AC 75/28 L. V.: 0/3|