|Place of Origin:||China|
|Brand Name:||Pearl Electric|
|Certification:||IEC60076-11 ISO9001 ISO14001 KEMA CE|
|Model Number:||SFSZ11-40 MVA 110 KV|
|Minimum Order Quantity:||negotiation|
|Packaging Details:||Wooden Package, suitable for 20'/40' container|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram|
|Product Type:||Power Distribution Transformer||Rated Capacity:||40 MVA|
|Rated HV Voltage:||110 KV||Material:||Copper Material|
high power transformer,
industrial power transformer
110 kv 6.3mva power transformer with two windings in copper material
Power Distribution Transformer Quick Details
Power Distribution Transformer Accessories installation
According to “Bushing Installation & Instruction Manual”!
Unpack the bushing, do cleaning to remove the scraps from packaging.
Remove bushing panels and install the bushing following the instruction.
b) Install the test pipe for hydraulic seal. According to the needs of test, pre-install a 2-meter high hydraulic tube on teh cover, in order to make the final hydraulic seal test.
c) Protector connection.
Fill oil to the main body
After the installation of the transformer’s accessories, it needs oil filling. First open the lower valve of the radiator when fill the tanks, and the radiators are gradually filled with oil at the same time. When the radiators are full of oil, in order to exhaust the air at the tope completely, it needs to open the upper air plug to exhaust the air.
The action must be quick, lightly open the oil plug and closed it and spin tightly as soon as the oil begins to spill. Then open the upper valve of the radiator. When the oil is full, use the above-mentioned method to open deflate plug at the top of the bushing, ascending base, observing windows and other places one by one, deflate air and then close them.
Power Distribution Transformer Specification
|Type||Rated Capcity||Rated Voltage||Connection Symbol||No-load loss||load loss||no-load current||Impedance voltage|
Our main items: