|Place of Origin:||China|
|Brand Name:||Pearl Electric|
|Certification:||KEMA, CE, CCC, ISO9001|
|Model Number:||PEC-S, SC(B) 9-15|
|Minimum Order Quantity:||1 unit|
|Packaging Details:||Seaworthy wooden packing|
|Delivery Time:||30days-50days ex-work|
|Payment Terms:||T/T, L/C|
|Supply Ability:||9000 units per year|
High Efficency Dry Type Transformer Made With Epoxy Resin 2500 Kva-50 Kva
Dry Type Transformer Advantages:
Cast resin dry type transformer, eco-friendly, high efficiency.
Accessories : IP protective enclosure
The standard transformers produced by our company are without the case and their protection level is IP20.We can also provide IP30 or IP40 if you require.The case can be made by common steel plates,stainless steel plants or aluminium alloy and can be acid-washed,parkerised and powder-painted.
Accessories :Temperature controller
The temperature control displays are installed on the low voltage side of the case ,which are reliable and convenient for users to check.
1.OEM is available.
2.Your inquiry related to our product & price will be replied within 24 hours.
3.Well-trained & experienced staff are to answer all your inquiries in English
4.Working time: 8:00am ~17:00 pm, Monday to Friday. (UTC+8)
5.Customized solution & perfect after-sale service
6. Payment: we can accept T/T, L/C.
7. For large order, engineer can be sent to your country for on-site mainternace instructions.
1 Before equipment installation, please first refer to the following materials carefully: this manual, nameplate and overall dimensional drawings, thus to get familiar with the product’s total weight and installation methods and prepare corresponding lifting facility and special tools.
2 The transformer should be kept at least 300mm away from walls and other equipment during installation. Transformers installed side by side should have at least 300mm clearance.
3 The minimum safe distance between conductors and ground should conform to IEC76-3-1 POWER TRANSFORMERS-INSULATION LEVELS AND DIELECTRIC TEST-EXTERNAL CLEARANCES IN AIR.
4 The minimum safe distance between the HV coil and ground is listed as follows:
|Net distance (mm)||40||60||90||120||160||250|
5 Usually, the transformer can be placed directly onto the service site and then be put into operation after installation and inspection. If the transformer must be fastened in place for shock-proof purpose or if there are other special requirements, bolts should be embedded into the foundation. The position of the bolts should be in line with the installation holes of the transformer according to outline drawings. To secure the transformer, remove the wheels and bolt the transformer to the foundation.
6 The connections between live parts must be secure. The torque to be applied is listed as below:
|I Basic Information|
|1||Rated Voltage ratio||kV||50kV / 0.433 kV|
|II Electric Performance|
|2.05||Number of phase||Three|
|2.06||Insullation Class||Class H|
|2.07||Temperature Rise (@40℃ ambient temperature)||K||125K|
|2.14||Load Loss (@120℃)||W||20000|
|2.15||Local Partial discharge||pC||<10PC|
|2.16||Impulse Withstand Voltage (HV/LV)||kV||75/0|
|2.17||Power Frequency Withstand Voltage
|2.18||Rated Duration of Short Circuit||s||2|
|III Materials & Accessories|
|3.01||Core Materials||Silicon Steel Sheet|
|3.02||Winding Materials||Copper conductor/foil|
|3.03||Insulation methods||HV vacuum cast / LV impregnant|
|3.04||Main Insulation Materials||Epoxy Resin|
2 Applied Standard
GB/T10228 , GB1094.11 , IEC60076-11 , DIN42523
|Name:||Dry Type Transformer||Cooling:||AN Or Customized|
|Winding:||Two-winding Transformer||Rated H. V.:||2500 Kva-50 Kva|
|Rated L. V.:||Customized||Impedance:||6% Or Customized|