|Place of Origin:||China|
|Brand Name:||Pearl Electric|
|Certification:||KEMA, CE, CCC, ISO9001|
|Model Number:||PEC-S, SC(B) 9-15|
|Minimum Order Quantity:||1 unit|
|Packaging Details:||Seaworthy wooden packing|
|Delivery Time:||30days-50days ex-work|
|Payment Terms:||T/T, L/C|
|Supply Ability:||9000 units per year|
|Capacity:||10~2500KVA Or Customized||Rated H. V.:||11/10/10.5/ 6/Kv Or Customized|
|Rated L. V.:||0.4kv Or Customized||Impedance:||4~8% Or Customized|
dry type distribution transformer,
oil immersed type transformer
35kV - Class , Power Distribution , Reactor , Earthing , Oil Type , Two Windings
To precisely calculate resonance frequency and intensity and avoid cavity resonance generated by the core structure during operation, simulation analysis is carried out for core mould design. Flexible connections are made between core and coils, core and bogie. With these measures adopted, the noise level is reduced by 10~15dB compared with the international standard.
During the HV winding design, rational structure is adopted to improve the electric distribution. With the lighting impulse wave simulation calculation and analysis being carried out with special auxiliary software, product's anti-lightning impulse capacity is greatly improved.
For series reactor without accessories dismantled during the transportation, it can be put
into various tests immediately after the equipment arrives at customer site. Otherwise,
please mount the accessories such as the oil-reservoir.
While mounting the mercury thermometer or signal thermometer, please fill series
reactor oil into the thermometer pocket.
While mounting the dehydrating breather, please fill series reactor oil at the bottom of
the breather (for hanging-type dehydrating breather) and check the sealing rubber plate
at the top and bottom before the series reactor is put into service.
Assemble other accessories and components.
Open the radiator and oil-reservoir’s butterfly valves and fill in with qualified series
reactor oil until normal oil-level is reached (the actual oil-level is depending on the
environment temperature). When filling oil into the reservoir, please open all air release
plugs and seal it by plugging in while oil comes out.