|Place of Origin:||China|
|Brand Name:||Pearl Electric|
|Certification:||KEMA, CE, CCC, ISO9001|
|Model Number:||PEC-S, SC(B) 9-15|
|Minimum Order Quantity:||1 unit|
|Packaging Details:||Seaworthy wooden packing|
|Delivery Time:||30days-50days ex-work|
|Payment Terms:||T/T, L/C|
|Supply Ability:||9000 units per year|
|Core:||Core-type Transformer||Cooling:||AN Or ANAF|
|Capacity:||10~2500KVA Or Customized||Rated H. V.:||30 Kv Or Customized|
|Rated L. V.:||0.4kv Or Customized||Impedance:||4~8% Or Customized|
dry type distribution transformer,
oil immersed type transformer
30kV - Class , High Reliabtility , Dry Type Reator , Earthing , Stable Performance
Features & Advantages
To precisely calculate resonance frequency and intensity and avoid cavity resonance generated by the core structure during operation, simulation analysis is carried out for core mould design. Flexible connections are made between core and coils, core and bogie. With these measures adopted, the noise level is reduced by 10~15dB compared with the international standard.
During the HV winding design, rational structure is adopted to improve the electric distribution. With the lighting impulse wave simulation calculation and analysis being carried out with special auxiliary software, product's anti-lightning impulse capacity is greatly improved.
For product without special package or with only simple package, attentions should be
paid during transportation to avoid any rain, snow or other foreign subjects falling into
During transportation, product inclination should not be larger than 15°.
For product equipped with carriage, please dismantle the roller to avoid product
displacement during the transportation.
During product lifting, please lift the product by using the four padding block under the
four corners of the package bottom. If there is no package for the product or when lifting
the product from the package, please use the lifting lugs on the main body. Please be
noted that the angle between the wire rope should not be larger than 30°.
Inspection and Acceptance
After the product arrives at customer’s site, please inspect the product for acceptance.
Check the product nameplate to see whether the specifications specified on the
nameplate conform to those written in the contract, for example, product model, rated
power, rated voltage, rated current and etc..
Check the document accompanied with the product.
With reference to the packing list, check the components and accessories.
Check whether there is nay damage on the product and displacement of the component
of components. Check the cables to know whether there is any loosing, crack, insulation
damage or polluted.
After the inspection for acceptance and if the product will not be put into service immediately,
please re-pack the product and store it in a safe place, thus to equipment safety.