|Place of Origin:||China|
|Brand Name:||Pearl Electric|
|Certification:||KEMA, CE, CCC, ISO9001|
|Model Number:||PEO-S, S9~13,SZ11-M,SZ11|
|Minimum Order Quantity:||1 unit|
|Packaging Details:||Seaworthy wooden packing|
|Delivery Time:||45-50days ex-work|
|Payment Terms:||T/T, L/C|
|Supply Ability:||2.5 Million KVA/Year|
|Capacity:||6300~63000kVA Or Customized||Rated H. V.:||110kv Or Customized|
|Rated L. V.:||33kV/11kV Or Customized||Vector Group:||Dyn11 Or Customized|
|Impedence:||8-10% Or Customized||Cooling:||ONAN / ONAF Or Customized|
three phase power transformers,
electrical power transformer
110kV - 50000kVA , Power Distribution Transformer , Three Phases , Power Transformer , Hight Capacity
The core is manufactured with high quality cold rolled grain-oriented silicon steel of high magnetic conductivity, and 45° mitring and steps overlapping structure is used for core production, enable the effectiveness of reducing no-load loss and no-load current.
HV winding is manufactured with high quality copper conductor, adopting optimized structure to improve electric distribution. Lightning impulse wave process is carried out for calculation and analysis, thus to improve transformer's anti-lightning impulse capability.
LV winding is manufactured with high quality foil conductor, so the ampere-turn balance is excellent and the transverse magnetic flux leakage is low. The anti-short circuit capability is thus greatly improved. Oil conduit is rationally designed in the windings to increase winding's heat dispersion surface, effectively reduce temperature and improve transformer's overload capability.
|By winding number||
110kV class 3-phase two-winding power transformer
110kV class on-load tap-changing power transformer
110kV class off-load tap-changing power transformer
Fill oil to the main body
After inspecting and filling oil conservator as prescribe until the oil surface is on the normal oil level, close the connected pipe valves between oil conservator and tanks, fill oil in hydraulic pipe until the oil surface is over 1.5m above the cover, then do the oil sealing pressure check after assembly, the test time shall not be less than three hours.
Test (transformer should be done with the following tests after the installation)