Payment & Shipping Terms:
|Capacity:||6300~63000kVA Or Customized||Rated H. V.:||110kv Or Customized|
|Rated L. V.:||33kV/11kV Or Customized||Vector Group:||Dyn11 Or Customized|
|Impedence:||8-10% Or Customized||Cooling:||ONAN / ONAF Or Customized|
110kV - Class , Power Distribution Transformer , Three Phases , Power Transformer , Hight Capacity
|By winding number||
110kV class 3-phase two-winding power transformer
110kV class on-load tap-changing power transformer
110kV class off-load tap-changing power transformer
4.1 Pay attention to the follows while transporting:
l Weight, size, hanging height, etc. can be found in the reference drawings.
l If flatbed truck is used for transporting, should check its loading record in the past.
l Fix the transformer body on the flatbed truck with rope through fixing holes. Refer to reference drawings for the locations of those holes.
l Attention! There is special axis for hanging and pedestal for hoisting jack. Use them while hanging and carrying the transformer, no use with other places.
l The ropes must be long enough to ensure the hanging angle is less than 30 degrees. Balance girder should be used due to limit of space height.
l Only the special holes can be used while the transformer is being haled. No for ramp with gradient over 15 degrees or speed exceed 20km/h.
Different parts should be used for different carrying methods (such as hanging, hauling and moving). They are shown as follows:
|Hanging axis||4||On the lower tank||Full hanging|
|4||Bottom of the tank||Bi-directional traction or moving|
|Traction hole||4||Lower part of the tank|
|Jack block||4||Body of the tank||Hydraulic lifting|
Attention: Where transporting, don’t damage the buildings.