Payment & Shipping Terms:
|Core:||Silicon Steel Sheet||Cooling:||AN Or Customized|
|Winding:||Two-winding Transformer||Capacity:||3000KVA Or Customized|
|Rated H. V.:||11Kv Or Customized||Rated L. V.:||0.433kv Or Customized|
11kV - 3000kVA , Cast Resin Dry Type Transformer , Three Phases , Two Winding , Power Distribution
Cast resin dry type transformer, eco-friendly, high efficiency.
Cast-resin dry-type transformer, low noise, low loss and low partial discharge.
It canbe widely used in high-rise buildings,airports,stations,wharfs,power plants and transformer substations and are especially suitable for buildings with strict fire resistance requirements,such as flammable and combustible buildings.
Long time shipment & Seaworthy wooden box
1,Experience sale manager and quick response in before-sales
2,Excellent service in production time update with each proccession
3,Reliable quality to solve you aftersale headache
4,Long period for 1-2year subject to need that you can buy without hesitation.
1,Why I buy Pearl Electric' transformer
High quality, quick delivery and solid packing that will be your best choice.
2,Guantee & waranty
18 months after delivery or 12month after site operation.
3,Is that possible to be one of distributor of Pearl Electric in my country?
Yes,welcome any qualified and fare business partner to achieve win-win .
Feel free to contact you you will get immediately reply
1 The transformer can be transported by train, ship, truck or plane. The vehicle should be kept clean and relatively free of dust.
2 The transformer should be secured to the vehicle. Swinging, jarring or shifting during transportation should be avoided.
3 Supplementary accessories, parts, and document are packaged separately and delivered together with the transformer.
4 Products without packages should be secured to the vehicle by binding through the holes in wheels, clamps or lifting lugs. Binding on the coils, insulators, supporting blocks or cables is strictly prohibited.
5 Angle of inclination for transportation must be less than 30o.
6 Stacking of transformers is not allowed during transportation or storage. Use wood blocks not less than 100mm high to support the transformer during transit at port or storage at destination.
Inspection should be carried out immediately after the transformer arrives at the site. The following items are to be checked:
1 Whether parameters on the nameplate conform to those indicated in the contract, for example: type No., rated voltage, connection symbol, impedance voltage, etc.
2 Whether documents are complete.
3 Whether assembly parts packed with transformer comply with the packing list.
4 Whether any damage or misalignment has occurred during transportation; whether any connections have become loose or cracked; whether insulation layers are damaged; whether there are any foreign objects or dirt. In addition, remove wooden spacers used for transportation, if any.
5 Re-pack the transformer after inspection unless it will be installed immediately, and store it in a safe weatherproof location to avoid damage or theft.
6 If serious damage is found on the packaging or product, inform the transportation company and insurance company immediately and protect the goods from further handling.
|I Basic Information|
|1||Rated Voltage ratio||kV||11kV / 0.433 kV|
|II Electric Performance|
|2.05||Number of phase||Three|
|2.06||Insullation Class||Class H|
|2.07||Temperature Rise (@40℃ ambient temperature)||K||125K|
|2.14||Load Loss (@120℃)||W||22000|
|2.15||Local Partial discharge||pC||<10PC|
|2.16||Impulse Withstand Voltage (HV/LV)||kV||75/0|
|2.17||Power Frequency Withstand Voltage
|2.18||Rated Duration of Short Circuit||s||2|
|III Materials & Accessories|
|3.01||Core Materials||Silicon Steel Sheet|
|3.02||Winding Materials||Copper conductor/foil|
|3.03||Insulation methods||HV vacuum cast / LV impregnant|
|3.04||Main Insulation Materials||Epoxy Resin|
2 Applied Standard
GB/T10228 , GB1094.11 , IEC60076-11 , DIN42523