Payment & Shipping Terms:
|Cooling:||AN Or Customized||Winding:||Two-winding Transformer|
|Capacity:||1250KVA Or Customized||Rated H. V.:||11Kv Or Customized|
|Rated L. V.:||0.433kv Or Customized||Standard:||IEC60076|
11kV - 1250kVA Cast Resin Dry Type Transformer, Three Phases, Two Winding, Power Distribution
As per IEC60076 standard required, cast resin dry type transformer designed and manufactured by Pearl Electric is welcomed in home and abroad with features of low loss, artistic apearnce and compact size.
Scientific computing tools:
We use advanced electric, magnetic, thermal and mechanical computing software to calculate electro-magnetic field and magnetic flux leakage distributions, to analyzewave processes, and to select reliable insulation margin, thus to guarantee product reliability, enable low noise level,clamp-proof,anti-fouling,high mechanical strength, flame resisting, strong overload ability and low partial discharge quality.
Cast Resin Dry Type Transformer, Low Noise, Low Loss and Low Partial Discharge.
They are application to power transmission and distribution system,hotel,restaurant,commercial building,stadiums,chemical plants,stations,aiports,offshore drilling platforms,especially to heavy load centers and places with special fire protection requirements
1 If temporary storage is necessary, the package should not be removed. If it is dismantled for acceptance inspection, repackaging should be made afterwards.
2 For storage for a longer period, the transformer should be stored in a warehouse, which is clean, dry, and free of chemical or corrosive materials.
3 The transformers should not be stacked.
4 For temporary outdoor storage, transformer should be put on wooden spacers at least 100mm high.
1 Check whether any fixed parts and connections have become loose. Re-tighten them if necessary.
2 Check whether all parts assembled after transport are in good condition and whether any alien objects have become lodged inside the transformer (especially the air ducts). If excessive dust has accumulated on the transformer, clear it in accordance with section 11.2.
3 Check whether the fans, temperature control devices and other accessories can function normally. Pay attention to the direction of rotation of the fans if there is a three-phase power source. Usually, air is blown up into the coil from the bottom. If not, the phase sequence of the power source should be changed. Refer to the cooling system instructions for details. For temperature control and indication system and other accessories, wire connection should be done according to the
|I Basic Information|
|1||Rated Voltage ratio||kV||11kV / 0.433 kV|
|1.02||Applicable Standards||IEC 60076|
|1.04||Country of Origin||China|
|II Electric Performance|
|2.05||Number of phase||Three|
|2.06||Insullation Class||Class H|
|2.07||Temperature Rise (@40℃ ambient temperature)||K||125K|
|2.14||Load Loss (@120℃)||W||11300|
|2.15||Local Partial discharge||pC||<10PC|
|2.16||Impulse Withstand Voltage (HV/LV)||kV||75/0|
|2.17||Power Frequency Withstand Voltage|
|2.18||Rated Duration of Short Circuit||s||2|
|III Materials & Accessories|
|3.01||Core Materials||Silicon Steel Sheet|
|3.02||Winding Materials||Copper conductor/foil|
|3.03||Insulation methods||HV vacuum cast / LV impregnant|
|3.04||Main Insulation Materials||Epoxy Resin|
2 Applied Standard
GB/T10228 , GB1094.11 , IEC60076-11 , DIN42523
Contact Person: Sandy