|Place of Origin:||China|
|Brand Name:||Pearl Electric|
|Certification:||KEMA, CE, CCC, ISO9001|
|Model Number:||PEC-S, SC(B) 9-15|
|Minimum Order Quantity:||negotiation|
|Packaging Details:||Seaworthy wooden packing|
|Delivery Time:||50-60days ex-work|
|Payment Terms:||T/T, L/C|
|Supply Ability:||9000 units per year|
|Core:||3600kva 37 Kv||Cooling:||AN Or ANAF|
|Capacity:||10~2500KVA Or Customized||Rated H. V.:||37/Kv Or Customized|
|Rated L. V.:||0.4kv Or Customized||Impedance:||4~8% Or Customized|
compact transformer substation,
step up and step down transformer
35 kV - Class , Dry Type Transformer , Eco - Friendly , Prefabricated Substation , Europe Type , Compact Sub
Introduction of Pre-fabricated Substation.
Pearl Electric's history may date back to the year of 1958 when it is founded as the Panyu Electrical Motor Factory. With more than fifty years development and company restructuring/reorganization in recent years, Pearl Electric is now ready to realize its ambition of becoming a global power transformer manufacturer and supplier.
When lifting the product from the bottom, there are two ways: one is to use the wire ropes to hook the lifting eyes at the bottom of the enclosure and thread the rope through the check rings, the other is to use special lifting tool. Please see the following picture for these two methods. The lifting eye has two structures, one is stationary type and the other is the concealed type. Stationary lifting eye is welded onto the bottom of the enclosure and can not be moved. The concealed lifting eye can move and hide inside the enclosure. Before lifting, pull the lifting eyes out and the push them into t he enclosure after lifting operation.
When lifting the equipment, please lay some soft cloth or paper board between the wire rope and product enclosure surface, thus to avoid damage to product coatings.
In case that the product is still in the package, please lift the product from the product together with the package from the four corners marked with lifting symbols.