|Place of Origin:||China|
|Brand Name:||Pearl Electric|
|Certification:||KEMA, CE, CCC, ISO9001|
|Model Number:||PEO-S, S9~13|
|Minimum Order Quantity:||negotiation|
|Packaging Details:||Seaworthy wooden packing|
|Delivery Time:||35~50days ex-work|
|Payment Terms:||T/T, L/C|
|Supply Ability:||4000 units per year|
|Capacity:||2760 Kva Or Customized||Rated H. V.:||10kv Or Customized|
|Vector Group:||Dyn11 Or Customized||Impedence:||4%-6% Or Customized|
|Cooling:||ONAN/ONAF Or Customized|
dual voltage transformer,
step up and step down transformer
OEM Prefabricated Substations Transformers With Desirable Environment Adaptability
Prefabricated Substations manufactured by Pearl is the latest product developed on the basis of absorbing the most advanced technology and advantages of the similar products while considering customer's special practical operation habits. It features low loss, small size, easy installation and maintenance and low engineering cost. It can be installed both indoor and outdoor.
Prefabricated Substations Parameters
|Rated H.V.:||20 (20.5, 22)kV, ±2×2.5%|
|Notes: The above specifications may be customized according to customer's requirement.|
Prefabricated Substations Functions and Advantages:
1. High safety protection
2. Complete functions and reliable performance
3. Flexible structure
5. Low power consumption and energy saving
.. After acceptance inspection and before being putting into service, the transformer
should be stored in dry and well-ventilated place.
.. Please adopt correct ways for lifting the equipment.
.. Before putting the equipment into service, please ensure that the elbow cable plug and
elbow lightning rod is reliably plugged into their sockets. Improper plugging-in will
pose great hazards to the equipment.
.. The elbow cable plug and elbow lightning rod must be reliably earthed.
.. For a transformer equipped with off-load tap changer, on-load tap switching is
.. Please use the insulated operation rod when carrying out such operations as earthing,
testing, isolating or switching on/off.
.. Operations to plug-in type fuse must be carried out in off-circuit state.
.. The load switch can only disconnect the rated current, but not the short-circuit current.
.. Long-time overload operation will affect the service life of the transformer.
.. Please follow all the instructions described in this manual when carrying out operations
related with product safety.